What is CLX cable used for?
C-L-X is used for instrumentation, control, low voltage and medium voltage power circuits. C-L-X is well recognized by the National Electrical Code. It is recognized in Article 330 “Metal-Clad Cable,” as a factory assembly of one or more insulated circuit conductors in a corrugated metallic tube.
Table of Contents
How often should MC cable be supported?
According to NEC Article 330.30, MC cable must be supported and secured at intervals of 6 feet or less (unless routed through a framing member) and cables containing four or fewer conductors sized no larger than 10 AWG must be secured within 12 inches of every termination.
Is MC cable allowed in commercial buildings?
MC Cable Permitted Uses MC Cable, when listed and labeled for use, can be a wiring method in locations such as: Commercial, industrial, and residential/commercial buildings.
Can you use J hooks to support MC cable?
Among them, J Hooks are a flexible, efficient and economical solution for support especially when cables are required to install in confined areas that cannot accommodate cable trays or raceways….What Are J Hooks Used for?
|Cable Media Tyeps
|Low voltage cabling
|Power and control tray cable
Is MC cable safer than Romex?
Safety: Compared to Romex, MC cable is safer to install due to its metallic sheath. This sheath helps protect against accidental shearing and penetration, reducing the risk for accidental wire exposure. Romex sheathing is easily penetrated or sheared, making it less safe unless run through protective conduit.
Can Romex be used in a commercial building?
Romex is permitted in commercial buildings that are categories 3, 4, and 5. If put in conduit, romex may be installed in type 1 and type 2 construction.
Can you use armored cable outdoors?
These cables can be installed either indoors or outdoors and in exposed and concealed locations. They can be direct buried, where identified for such use. They can be installed in a cable tray or in any raceway. The cables can be installed as open runs or as an aerial cable on a messenger wire.
Can you run armored cable inside conduit?
Moderator. We would never install armored cable in a conduit.
What is Type MC HL cable?
Type MC HL is the metal-clad cable used in hazardous locations. According to the National Electric Code, the cable is suitable for hazardous locations in voltage between 600 V and 35 kV.
What is ITC cable?
NWI’s ITC or Instrumentation Tray Cable is engineered to meet or exceed application requirements for factory floor automation equipment, material handling, sensors and transducers, process controls and other applications.
Can you use staples to secure MC cable?
A. The rules for securing and supporting Type MC cable can be found in Section 330.30 of the Code. The requirements can be summarized as follows: Type MC cable must be supported and secured by staples, cable ties, straps, hangers, or similar fittings, designed and installed so as not to damage the cable.